The ebook FEEE  Fundamentals of Electrical Engineering and Electronics is based on material originally written by T.R. Kuphaldt and various coauthors. For more information please read the copyright pages. 
Home AC Polyphase AC Circuits Threephase power systems  
Search the VIAS Library  Index  
Threephase power systemsThreephase Polyphase Threewire DC systemSplitphase power systems achieve their high conductor efficiency and low safety risk by splitting up the total voltage into lesser parts and powering multiple loads at those lesser voltages, while drawing currents at levels typical of a fullvoltage system. This technique, by the way, works just as well for DC power systems as it does for singlephase AC systems. Such systems are usually referred to as threewire systems rather than splitphase because "phase" is a concept restricted to AC. But we know from our experience with vectors and complex numbers that AC voltages don't always add up as we think they would if they are out of phase with each other. This principle, applied to power systems, can be put to use to make power systems with even greater conductor efficiencies and lower shock hazard than with splitphase. Suppose that we had two sources of AC voltage connected in series just like the splitphase system we saw before, except that each voltage source was 120^{o} out of phase with the other: Since each voltage source is 120 volts, and each load resistor is connected directly in parallel with its respective source, the voltage across each load must be 120 volts as well. Given load currents of 83.33 amps, each load must still be dissipating 10 kilowatts of power. However, voltage between the two "hot" wires is not 240 volts (1200°  120180^{o}) because the phase difference between the two sources is not 180^{o}. Instead, the voltage is: Nominally, we say that the voltage between "hot" conductors is 208 volts (rounding up), and thus the power system voltage is designated as 120/208. If we calculate the current through the "neutral" conductor, we find that it is not zero, even with balanced load resistances. Kirchhoff's Current Law tells us that the currents entering and exiting the node between the two loads must be zero:
So, we find that the "neutral" wire is carrying a full 83.33 amps, just like each "hot" wire. Note that we are still conveying 20 kW of total power to the two loads, with each load's "hot" wire carrying 83.33 amps as before. With the same amount of current through each "hot" wire, we must use the same gage copper conductors, so we haven't reduced system cost over the splitphase 120/240 system. However, we have realized a gain in safety, because the overall voltage between the two "hot" conductors is 32 volts lower than it was in the splitphase system (208 volts instead of 240 volts). The fact that the neutral wire is carrying 83.33 amps of current raises an interesting possibility: since it's carrying current anyway, why not use that third wire as another "hot" conductor, powering another load resistor with a third 120 volt source having a phase angle of 240^{o}? That way, we could transmit more power (another 10 kW) without having to add any more conductors. Let's see how this might look: Superposition Theorem Theorem, SuperpositionA full mathematical analysis of all the voltages and currents in this circuit would necessitate the use of a network theorem, the easiest being the Superposition Theorem. I'll spare you the long, drawnout calculations because you should be able to intuitively understand that the three voltage sources at three different phase angles will deliver 120 volts each to a balanced triad of load resistors. For proof of this, we can use SPICE to do the math for us:
120/208 polyphase power system v1 1 0 ac 120 0 sin v2 2 0 ac 120 120 sin v3 3 0 ac 120 240 sin r1 1 4 1.44 r2 2 4 1.44 r3 3 4 1.44 .ac lin 1 60 60 .print ac v(1,4) v(2,4) v(3,4) .print ac v(1,2) v(2,3) v(3,1) .print ac i(v1) i(v2) i(v3) .end VOLTAGE ACROSS EACH LOAD freq v(1,4) v(2,4) v(3,4) 6.000E+01 1.200E+02 1.200E+02 1.200E+02 VOLTAGE BETWEEN "HOT" CONDUCTORS freq v(1,2) v(2,3) v(3,1) 6.000E+01 2.078E+02 2.078E+02 2.078E+02 CURRENT THROUGH EACH VOLTAGE SOURCE freq i(v1) i(v2) i(v3) 6.000E+01 8.333E+01 8.333E+01 8.333E+01 Sure enough, we get 120 volts across each load resistor, with (approximately) 208 volts between any two "hot" conductors and conductor currents equal to 83.33 amps. At that current and voltage, each load will be dissipating 10 kW of power. Notice that this circuit has no "neutral" conductor to ensure stable voltage to all loads if one should open. What we have here is a situation similar to our splitphase power circuit with no "neutral" conductor: if one load should happen to fail open, the voltage drops across the remaining load(s) will change. To ensure load voltage stability in the even of another load opening, we need a neutral wire to connect the source node and load node together: So long as the loads remain balanced (equal resistance, equal currents), the neutral wire will not have to carry any current at all. It is there just in case one or more load resistors should fail open (or be shut off through a disconnecting switch). Polyphase ThreephaseThis circuit we've been analyzing with three voltage sources is called a polyphase circuit. The prefix "poly" simply means "more than one," as in "polytheism" (belief in more than one deity), polygon" (a geometrical shape made of multiple line segments: for example, pentagon and hexagon), and "polyatomic" (a substance composed of multiple types of atoms). Since the voltage sources are all at different phase angles (in this case, three different phase angles), this is a "polyphase" circuit. More specifically, it is a threephase circuit, the kind used predominantly in large power distribution systems. Let's survey the advantages of a threephase power system over a singlephase system of equivalent load voltage and power capacity. A singlephase system with three loads connected directly in parallel would have a very high total current (83.33 times 3, or 250 amps: This would necessitate 3/0 gage copper wire (very large!), at about 510 pounds per thousand feet, and with a considerable price tag attached. If the distance from source to load was 1000 feet, we would need over a halfton of copper wire to do the job. On the other hand, we could build a splitphase system with two 15 kW, 120 volt loads: Our current is half of what it was with the simple parallel circuit, which is a great improvement. We could get away with using number 2 gage copper wire at a total mass of about 600 pounds, figuring about 200 pounds per thousand feet with three runs of 1000 feet each between source and loads. However, we also have to consider the increased safety hazard of having 240 volts present in the system, even though each load only receives 120 volts. Overall, there is greater potential for dangerous electric shock to occur. When we contrast these two examples against our threephase system, the advantages are quite clear. First, the conductor currents are quite a bit less (83.33 amps versus 125 or 250 amps), permitting the use of much thinner and lighter wire. We can use number 4 gage wire at about 125 pounds per thousand feet, which will total 500 pounds (four runs of 1000 feet each) for our example circuit. This represents a significant cost savings over the splitphase system, with the additional benefit that the maximum voltage in the system is lower (208 versus 240). One question remains to be answered: how in the world do we get three AC voltage sources whose phase angles are exactly 120^{o} apart? Obviously we can't centertap a transformer or alternator winding like we did in the splitphase system, since that can only give us voltage waveforms that are either in phase or 180^{o} out of phase. Perhaps we could figure out some way to use capacitors and inductors to create phase shifts of 120^{o}, but then those phase shifts would depend on the phase angles of our load impedances as well (substituting a capacitive or inductive load for a resistive load would change everything!). Alternator GeneratorThe best way to get the phase shifts we're looking for is to generate it at the source: construct the AC generator (alternator) providing the power in such a way that the rotating magnetic field passes by three sets of wire windings, each set spaced 120^{o} apart around the circumference of the machine: Pole, alternatorTogether, the six "pole" windings of a threephase alternator are connected to comprise three winding pairs, each pair producing AC voltage with a phase angle 120^{o} shifted from either of the other two winding pairs. The interconnections between pairs of windings (as shown for the singlephase alternator: the jumper wire between windings 1a and 1b) have been omitted from the threephase alternator drawing for simplicity. Y configuration Star configurationIn our example circuit, we showed the three voltage sources connected together in a "Y" configuration (sometimes called the "star" configuration), with one lead of each source tied to a common point (the node where we attached the "neutral" conductor). The common way to depict this connection scheme is to draw the windings in the shape of a "Y" like this: The "Y" configuration is not the only option open to us, but it is probably the easiest to understand at first. More to come on this subject later in the chapter.


Home AC Polyphase AC Circuits Threephase power systems 