Electrical Engineering is a free introductory textbook to the basics of electrical engineering. See the editorial for more information.... 
Home Polyphase Circuits Combined Delta and Wye Loads  
Search the VIAS Library  Index  
Combined Delta and Wye LoadsAuthor: E.E. Kimberly At its worst, a problem of calculating line currents may involve one or more delta loads, one or more wye loads, and one or more singlephase loads connected between one line and any other line, including the neutral line if there is one. Unbalanced wyeconnected loads are extremely rare, and their solutions are relatively so complicated that they will be neglected entirely in the general case of unbalance in line currents. Every problem involving unbalanced deltaconnected loads and miscellaneous singlephase loadings can be solved by the methods used with the balanced deltaconnected load; but, inasmuch as currents at a delta point will almost never be just 60° apart in phase, the factor cannot be used.
Example 91.  As indicated in Fig. 94 (a), a factory load consists of the following: One department with seven 10hp motors, 3phase, 60cycle, 230volt, all of
which together draw 190 amp per line lagging their respective linetoneutral
voltages by 58°. One department with a lighting load of 90 amp at 100 per cent power factor
between lines 1 and 2. One department with a total load of 50 amp at 70.7 per cent power factor, lagging,
connected between lines 2 and 3. One department with a total load of 80 amp at 80 per cent power factor, leading,
connected between lines 3 and 1.
Calculate the line currents I_{1}, I_{2}, and I_{3} in lines 1, 2, and 3 with a phase sequence of E_{3}2, E_{2}1, E_{1}3
Solution.  The vector diagram is shown in Fig. 94 (b). The currents in line 1 may be combined as follows:
If the phase sequence of the voltages applied to the load is reversed by reversing any two of the leads, then the currents in those lines will be reversed. In assembling the vectors for addition at any corner of the voltage triangle to find the corresponding line current, all current vectors associated with voltage vectors positive to the point must be taken as positive and all current vectors associated with voltage vectors negative to the point must be taken as negative (reversed).


Home Polyphase Circuits Combined Delta and Wye Loads 